Constructed with soft-drawn copper, type THHN insulated conductors which are individually wrapped with a moisture-resistant, flame-retardant paper covering. Interlocking steel armor is applied over the assembly. A 16 AWG aluminum bond wire is placed inside the armor, runs longitudinally and is in intimate contact with the armor for its entire length. General applications: Dry locations only, branch, feeder, and service power distribution in commercial, industrial, institutional, and multi-residential buildings, power, lighting, control and signal circuits, concealed or exposed installations, installed in cable tray and approved raceways, environmental air-handling spaces per NEC and under raised floors for information technology equipment Conductors And Cables Per NEC 645.5(D) & 645.5(D)(2). 300.22(C), Fished Or Embedded In Plaster.
Meets Or Exceeds The Requirements Of UL Standard 4 For Armored Cable, UL Standard 83, Federal Specification A-A59544 (Formerly J-C-30B), And The National Electrical Code. Listed For Use In UL 1, 2, And 3 Hour Through-Penetration Firestop Systems.